(Only available with Flow Telemetry Add On Option at time of purchase)
It should be understood that in order for the NETB15PPP to properly record and log flow, the NETB15PPP MUST OBSERVE AT LEAST 3 PULSES PER MINUTES AT THE LOWEST LIKELY FLOW SCENARIO.
Observing LED1 is a good way of determining if the minimal pulse threshold is being met, even at low flow rates. With dip switch 2 on, use a stop watch and count the number of pulses observed in a minute. If less than 3 are observed, the flow meter will need to be reconfigured to pulse at a more frequent rate.
It should be noted that the NETB15PPP does not support flow meters that use a 4-20mA output signal. Only digital pulse outputs are compatible.